Wilson Farm Tank Leak Locating
Wilson Farm is a 128-year-old family-run farm located in Lexington Ma with a second farm stand and fields in Litchfield NH. After the farm had a tank test failure during an annual test they decided to replace the diesel and gasoline underground storage tanks on site.
When the underground tanks were removed Jim Wilson questioned whether the 3000-gallon storage tanks were still under warranty because they looked in good condition. His insurance company confirmed they were and called CommTank to determine the source of the underground tank leak. CommTank had to do some preparation to test the underground tanks because they were already out of the ground. With the help of a forklift on site and four-inch plugs to seal off the tank top, we were able to test the tank and the interstitial space. Using our acoustic test we confirmed there was a breech in the integrity of the tank and our helium test pinpointed the source of the leak. The tank leak was found on the primary wall tank bottom and coverage by the insurance company was confirmed.